Electric System Specifications Pdf, UNIT SHALL BE SURFACE MOUNTED • WITH CENTER.OF UNIT BETWEEN two’ 8° AND 6′ ABOVE FINAL GRADE.IN A LEVEL AND PLUMB POSITION. UNIT SHALL BE FASTENED TO BUILDING SECURELY USING LEAD ANCHORS (FOR BRICKAND CONCRETE), TOGGLE BOLTS (FOR WOOD SIDING) OR WOOD SCREWS (FOR two •x4• STUDS, LOG WALLS, OR OTHER SOLID LUMBERl.ALL SCREWS OR BOLTS SHALL BE 114• DIAMETER (MIN.) STAINLESS STEEL A MINIMUM OF FOUR FASTENERS SHALL BE USED TO MOl.WT SOCKET.
C.S SERVICE DROP ATTACHMENT, 1. DEVICE FOR ATTACHING SERVICE DROP TO BUILDING SHALL BE FURNISHED BY COMPANY AND INSTALLED SECURELY BY CUSTOMER (SEE PAGE 5.105 ) AT MNMUM VERTICAL CLEARANCE AS SHOWN BELOW. 2. F MINIMUM VERTICAL CLEARANCE CANNOT BE MANTANED WITH THE NSTALLATION OF AN ATTACHMENT BOLT AS SHOWN BELOW, THE CUSTOMER SHALL INSTALL A STEEL SERVICE MAST (SEE PAGES.105). 3. CONNECTIONS BETWEEN SERVICE DROP AND SERVICE ENTRANCE CONDUCTORS SHALL BE MADE (BY COMPANY PERSONNEU BELOW WEATHERHEAD, FORMING A DRIP LOOP.
DMCA Disclaimer: This site complies with DMCA Digital Copyright Laws. Please bear in mind that we do not own copyrights to these books. We’re sharing this material with our audience ONLY for educational purpose. We highly encourage our visitors to purchase original books from the respected publishers. If someone with copyrights wants us to remove this content, please contact us immediately.
All books on the ozielbook.com are free and YOU HAVE TO KNOW THAT WE DO NOT HOSTED ALL FILES ON OUR WEBSITE. If you feel that we have violated your copyrights, then please contact us immediately (click here).